When you need air conditioning, heating, plumbing or electrician services in Hiram GA, you need TE Certified. We have served your home maintenance needs for over 20 years!
We don’t quit until you’re 100% satisfied with our service. That’s why we’re one of the highest-rated companies in the Hiram GA area. Check out the many happy review from your neighbors to see why they choose TE Certified for their electrical, HVAC and plumbing service needs!
for Hiram, GA
Excellent customer care
Valerie - Hiram, GA 30141
Rebecca - Hiram, GA 30141
Great service and Cody was very good at explaining to me what was wrong & what he was doing. Highly recommend!
Ivette - Hiram, GA 30141
Joaquin was thorough in his evaluation of the issues presented to him. He checked various things to ensure that when he was finished, there would be no issue. Thank you!
Troubleshoot light not turning off in kitchen. Repaired bad tap.
Replace failed contactor inside the air handler system that help control the electric heat strips. Installed new double pull contactor in air handler, tested electric heat strip by themselves, tested normal heating operations, and monitored systems operations. System is operating properly at this time. Recommended adding wet switch to system for added water safety to help avoid water damage in the result of improper operations.
Performed a Homecare inspection.
Upon arrival the homeowner had informed me that they had tried to turn on the heat and the system then stopped and then the a/c wouldn’t come back on either. When inspecting the equipment I had found that the contactor located inside the air handler has failed and is popping the fuse as the electric heat strip are told to turn on. As temporary solution I then detached the auxiliary heat terminal to no longer try to energize the heat strips and went further into equipment to ensure temporary will be a viable option. After performing the rest of the inspection the heat pump will be able to maintain a comfortable temperature but as outdoor temperatures lower further into the winter the heat pump will begin to struggle without the auxiliary heat to help. Due to system reaching 8 years old i highly recommend considering replacing the equipment for better efficiency and effectiveness. 20x20x5 filter had been extremely clogged and had been replaced in 2022. Put a 20x20x1 filter as a temp
Toilet leaking and high water pressure. Pulled, rebuilt, and reset toilet. Also replaced service valve to toilet. Replaced pressure regulator, main shut off valve, and thermal expansion tank. Pressurized system and verified.
Home Inspection Removed and replaced the damaged breaker in the main panel.
Lighting Inspection Removed and replaced a burnt outlet in the living room.
System not cooling gave customer options
Inspected the home and pulled a permit for the power company to restore power and fixed the immediate issues that would need to be repaired before power could be restored.
Performed diagnostic on whole home system to ensure proper operations and to help limit worry of disruption during operations.
Installing Tesla car charger with search protection, lovely customers to work with
Install new toilet